5.0/5 Ton Horizontal Geothermal heat pump 22.0 EER
WARRANTY:- 10 YEARS ALL PARTS
Unit Model HPX060HSS
5.0/5 Ton Horizontal Geothermal heat pump 22.0 EER
- FEATURE INFORMATION
- UNIT PERFORMANCE
How 5.0/5 Ton Horizontal Geothermal Heat Pump USA Works
Most geothermal systems installed in more rural areas use Horizontal Geothermal heat pump. This is because it takes a lot of lands to build a horizontal loop geothermal system. Customers may occasionally save money installing horizontal loops because less drilling is needed. Although ideal levels are believed to be 6-10 feet deep, the depth of the trenches needed to install a horizontal loop only needs to be 2-3 feet, or below the freeze line.
Higher efficiency than vertical ground loops
Installing can be much less expensive
Commonly believed to require less upkeep
Why Use a 5.0/5 Ton Horizontal Geothermal Heat Pump USA
Because they draw on the natural, free heat that exists beneath the ground, geothermal heat pumps are significantly more advantageous than conventional heating and cooling systems. They perform at their highest level of efficiency when cooling your house. Homeowners benefit from efficient operation because it reduces pollution, saves money and energy, and promotes environmental preservation.
Geothermal heat pumps not only help to lower energy and financial costs, but also air pollution. Additionally, they are better at cooling the house.
How Geothermal Heat Pump Works in Seasons
The geothermal heat pump draws heat from the ground heat exchanger during the winter and transfers it to the building’s air transfer system, which maintains the home’s comfortable temperature. The cycle is reversed in the summer. The ground heat exchanger receives heat from the geothermal heat pump that is extracted from the air inside the building. The earth receives the heat from the heat exchanger. Homeowners can get free hot water all summer long by using the heat that is extracted from inside the building during the summer.
5.0/5 Ton Horizontal Geothermal Heat Pumps are a renewable energy source
5.0-ton Horizontal geothermal heat pump systems offer a plethora of advantages. They start by using heat that naturally occurs underground as a renewable energy source. Seasons have no bearing on this heat, so they will be available indefinitely. You won’t have to worry about air pollution, which is a factor in the development of fatal respiratory diseases, because the energy is clean and green as well. Geothermal systems are particularly durable, above all. The loops have a remarkable 56-year warranty and have a lifespan of more than 50 years. The fact that you can benefit from geothermal energy for the rest of your life is highlighted by this long-term warranty alone.
Buy a 5.0/5 Ton Horizontal Geothermal Heat Pump 22.0 EER at Miamihp
Purchase the 5.0 and 5 Ton Horizontal Geothermal Heat Pumps with 22.0 EER, Stainless Steel, and Drain Pain. Miami Heat Pump manufactures effective horizontal geothermal heat pumps based on your requirements. In the winter, it uses the earth as a heat source to absorb heat, and in the summer, it sinks heat. The temperature below six meters from the earth’s surface is roughly constant at between ten and sixteen degrees Celsius, depending on latitude and longitude. Horizontal water-to-air heat pumps can achieve relatively high temperatures for both summer cooling and winter heating. Better than conventional cooling or heating pumps, centralized cooling, and heating systems. The highest tonnage horizontal geothermal heat pump for your needs is what this design takes advantage of by capitalizing on those advantages.
Geothermal heat pumps are more and more in demand
A ground-source heat pump (GSHP) typically produces four to five kilowatts of heat for every kilowatt of electricity used, as they only use electricity to move heat, not to create it. Three to four of these kilowatts of heat are clean, free, and renewable because they are extracted from the earth itself. These heat pumps use factory-sealed refrigeration systems, which the IGSHP claims minimize ozone layer destruction and require little to no recharge. The system also keeps a home’s interior air cleaner and free of pollen, outdoor pollutants, mold spores, and other allergens because it doesn’t rely on outside air.
According to the Geo-Heat Center at the Oregon Institute of Technology, demand for geothermal heat pumps is rising at a rate of about 20% annually. The industry can only handle the growth of that magnitude for the time being. The difficulty the industry is having meeting demand for the equipment, contractors, drillers, and other trained workers was recently brought to light in a New York Times article.
Horizontal Geothermal Heat Pump Unit Performance
EVAP Cooling Capacity: 60,000 BTU
HR Heating Capacity: 70,000 BTUHR (Heat Pump Mode)
Face Velocity: 334
Coil Entering Air Temperature: 80.6/66.2
A Ton of Horizontal Geothermal Heat Pump Condensers’ Performance
Entering water temperature: 86.0 WLHP 15.0 WLPM water flow
H20 Drop-FT 4.5 water press
Arrangement of Blowers in a Horizontal Geothermal Heat Pump
1900 Air Volume-CFM
Blowers Size & QTY: 1010/1 Fan Motor-HP & QTY: 3/4/1 ESP-INH20: 0.6
Buy Get rid of all your cooling and heating requirements with the best configuration and excellent performance of 5-ton horizontal geothermal heat pumps 22.0 EER. Contact us today!
|CABINET-||Stainless steel, Insulated Evaporator Section, Access Panels|
|DRAIN PAN-||Stainless steel, Insulated|
|SAFETY-||High/Low press, Switches, Condensate Over Flow switch, Overload Protection, AntiShort Cycle Relays, Lock Out Relays|
|BLOWERS-||Centifugal Galvanized Wheel, X13 BLDC Motor|
|REF CIRCUITS-||Thermal Expension Valve 1 Circuit|
|COND COIL-||Coaxial Cupronickel Heat Exchanger|
|EVAP COIL-||Copper Tubes, Alumininium Fins|
|EVAP COOLING CAPACITY – BTU/HR||WLHP 60,000||GWHP 68,000||GLHP 63,000|
|HEATING CAP. – BTUIHR (HEAT PUMP MODE)||WLHP 70,000||GWKP 58,000||GLHP 45,000|
|FACE VELOCITY – FPM||334|
|COIL ENTERING AIR TEMP. DB/WB- F||80.6/66.2|
|AIR VOLUME – CFM||1900|
|BLOWER SIZE & QTY||10”x10” / 1|
|FAN MOTOR-HP&QTY||3/4 / 1||FLA(EA)= 6.0 A|
|WATER FLOW – GPM||15.0|
|ENTERING WATER TEMP. °F||WLHP 86.0||GWHP 59.0||GLHP 77|
|WATER PRESS. DROP – FT H2O||4.5|
|NO. OF CIRCUIT CAPACITY STEPS||1/1|
|TYPE & OTY||Scroll/1||RLA(EA)= 26.4 A||LRA(EA)=134.0 A|
|VOLTAGE RATING I PHASE / HERTZ||230/1/60|
|E.E.R.||WLHP 16.0||GWHP 22.0||GLHP 17.2|
|C.O.P (HEAT-PUMP ONLY)||WLHP 4.5||GWHP 4.1||GLHP 3.6|
|MIN AMP. / MAX FUSE – AMPS.||39/60|
|DIMENSION W” X L X H”||26” X 45.50” X 20.75”|
|WEIGHT – NET – LBS.||330|
|WATER CONNECTION SIZE||1″|
|DRAIN CONNECTION SIZE||3/4″|